Wednesday, November 15, 2006
1542 Tulane Ave :
- The contractor ran another line to power up the City Water pumps because the line they first ran could only handle running one pump at a time.
- The elevator equipment room has lights and power to the receptacles. Stratos can begin their work.
- Power has been restored to the print shop.
Dental School :
- Triton and Independence Specialist rechecked the pump motors and found the rotation was wrong on the units that had the vibration. Rotation was corrected and the pumps operated smoothly.