THURSDAY, SEPTEMBER 30, 2010
ALLIED HEALTH/NURSING BLDG PERMANENT REPAIRS & MITIGATION:
- The contractor prepped for the stucco installation tomorrow.
- Crews continued setting the raised platforms for the AHUs on the 1st Floor.
RESIDENCE HALL PERMANENT REPAIRS & MITIGATION:
- The electrical contractor continued installing conduits on the 2nd Floor.
- The contractor pressure washed the storage room on the 1st Floor, A-Tower.